Don't know all the details but 404.11 references 240.83:OH, I dint know that. I don't think it is marked as such. Good info.
Section 240.83(D) requires circuit breakers used as switches for fluorescent lighting circuits be listed and marked as SWD or HID.
So I think you're okay.